Fire control regulations for color steel plate room
I. departments at all levels shall cooperate with each other in the construction departments of cities and counties at all levels, public security fire departments and quality and technical supervision departments to strengthen coordination and cooperation.
The competent construction department and the public security fire department shall strengthen the supervision and management of the use of the color steel plate structure construction room on the construction site, and timely report the problems found
to the quality and technical supervision department. The quality and technical supervision department shall strengthen the supervision of color steel plate house in the production and circulation field by referring to the fire laws and regulations, so
as to avoid the flammable or combustible materials in the selected color steel plate thermal insulation materials.
Color steel plate
II. Reach a consensus on fire control. The whole society has reached a consensus on fire control safety. If
the quality is not qualified and it is not suitable to use color steel plate houses, please report to the relevant departments in time. At present, fire safety has become an important part of public safety, and has been paid more and more attention by
all walks of life. Everyone should take action to put an end to the hidden danger of fire.
he fire prevention measures for color steel houses are in place. The temporary color steel houses usually have large volume and many people, so evacuation
is very important. If there are many teaching floors, it is difficult to evacuate people in time. Therefore, the maximum allowable floor height should not exceed two floors. In order to prevent the color steel exterior walls and roof panels from becoming
the way of fire spread. The materials shall be non combustible; meanwhile, the fire hydrant system shall be set indoors. The fire department reminds: the color steel plate is best made of asbestos plate and fire-resistant cotton as fillers, which can
meet the fire safety conditions of the construction site only when the fire-resistant limit of class A is reached. In the use process, some heat sources and fire sources shall not be close to the color steel plate, and a certain distance shall be kept.
If the kitchen is to be set up in the color steel plate room, a thermal insulation layer is required, and the wall surface shall be equipped with a fireproof rock wool thermal insulation layer. Wires and cables shall not pass through the color steel plate.
If they need to pass through, they shall be provided with protective sleeves. Sockets and switch boxes shall be made of metal galvanized boxes and surface mounted. Simple fire-fighting equipment shall be equipped indoors and outdoors, and fire alarm shall
be installed if conditions permit, so as to facilitate rapid evacuation of personnel. A safe distance of at least 6 meters shall be kept between color steel plank houses.
Fire prevention method of color steel plate room
Fire experts pointed out that the following aspects should be paid attention to in how to prevent fire in color steel plate houses:
First of all, rock wool with good fire resistance shall
be used as core material for color steel plate, and polystyrene and polyurethane shall not be used as core material. After the completion of the plank house, no core materials shall be exposed at the external visible parts.
Secondly, in the process
of use, some heat sources and fire sources shall not be close to the steel plate, and a certain distance shall be kept.
Third, it is better not to cross wires and cables from the core material. If it is necessary to cross, a protective sleeve shall
be added. The socket and switch box shall adopt the metal galvanized box and the open installation method. Finally, the fire-fighting equipment should be in good condition and effective, and the personnel can operate skillfully. If possible, the fire
alarm should be installed to facilitate the rapid evacuation of personnel.